Email us or Call 1-800-723-2861
You should look for an easily attachable place where your transducer will move in conjunction with the interrupter(s). You should also try to mount the transducer to a solid piece of metal that won’t vibrate during operation of the circuit breaker. The closer you are to the interrupter without mechanical linkages in between, the more accurate your travel trace will become. Once a transducer mounting spot is established, you should continue to test it at this spot for accurate trending purposes.